Not available for Iranian market
The model AFS-303 is a general purpose proving switch with gold contacts designed for HVAC, Energy Management and DDC (Direct Digital Control) applications. Goldcontact switches are used in computer environments, direct digital control, or wherever low ampere currents are wired. AFS-303 can be used to sense positive, negative, or differential air pressure.
DESCRIPTION & OPERATION
The plated housing contains a diaphragm, a calibration spring and a snap-acting SPDT switch with gold contacts.The sample connections located on each side of the diaphragm accept ¼” OD metallic tubing via the integral compression nut and ferrule.
MOUNTING (Fig. 1)
Select a mounting location that is free from vibration. The AFS-303 must be mounted with the diaphragm in any vertical plane in order to obtain the lowest specified operating set point. Avoid mounting with the sample line connections in the “up” position. Surface mount via the two 3⁄16″ diameter holes in the integral mounting bracket. The mounting holes are 3-⅞” apart.
AIR SAMPLING CONNECTION (Fig.2)
The AFS-303 is designed to accept firm-wall sample lines of ¼”OD tubing by means of ferrule and nut compression connections. For lines up to 10 feet in length, ¼” OD tubing is acceptable. For lines up to 20 feet, use ¼” ID tubing. For lines up to 60 feet, use ½” ID tubing. A ¼”OD adapter, suitable for slip-on flexible tubing, is available: order part number 18311. Locate the sampling probe a minimum of 1.5 duct diameters downstream from the air source. Install the sampling probe as close to the center of the airstream as possible. Refer to Figure 2 to identify the high pressure inlet (H) and the low pressure inlet (L). Select from the five application options listed below, and connect the sample lines as shown.
POSITIVE PRESSURE ONLY: Connect the sample line to inlet H; inlet L remains open to the atmosphere.
NEGATIVE PRESSURE ONLY: Connect the sample line to inlet L; inlet H remains open to the atmosphere.
TWO NEGATIVE SAMPLES: Connect the higher negative sample to inlet L. Connect the lower negative sample to inlet H.
TWO POSITIVE SAMPLES: Connect the higher positive sample to inlet H. Connect the lower positive sample to inlet L.
ONE POSITIVE & ONE NEGATIVE SAMPLE: Connect the positive sample to inlet H. Connect the negative sample to inlet L.
ELECTRICAL CONNECTIONS (Fig.3)
Before pressure is applied to the diaphragm, the switch contacts will be in the normally closed (NC) position. The snap switch has ¼” 90º quick connect spade terminals. Wire alarm and control applications as shown in Fig.4.
The adjustment range of an AFS-303 Air Switch is 0.05 ±.02″ w.c. to 12.0″ w.c. To adjust the set point, turn the adjusting screw counterclockwise until motion has stopped. Next, turn the adjusting screw 4 complete turns in a clockwise direction to engage the spring. From this point, the next ten turns will be used for the actual calibration. Each full turn represents approximately 1.2″ w.c.
Please note: To properly calibrate an air switch, a digital manometer or other measuring device should be used to confirm the actual set point.
MODEL AFS-303 AIR FLOW PRESSURE SENSING SWITCH WITH GOLD CONTACTS
Mount with the diaphragm in any vertical plane.
Set Point Range:
0.05″ ± 0.02″ w.c. to 12.0″w.c.
Field Adjustable “Operate Range”:
0.07″w.c. to 12.0″ w.c.
Field Adjustable “Release Range”:
0.04″w.c. to 11.2″ w.c.
Approximate Switching Differential: Progressive, increasing from 0.02± 0.01″ w.c. at minimum set point to approximately 0.8″ w.c. at maximum set point.
Air, or combustion by-products that will not degrade silicone.
½ psi (0.03 bar)
Operating Temperature Range:
-40F to 180F (-40 to 82C)
100,000 cycles minimum at ½ psi maximum pressure each cycle and at maximum rated electrical load.
300 VA pilot duty at 115 to 277 VAC, 15 amps noninductive to 277 VAC, 10 ma at 5 VDC (applies to dry circuit applications).
Gold, ¼” 90º quick-connect spade terminals.
Sample Line Connectors:
Male, externally threaded 7⁄16″ 24 UNS 2A thread, complete with nuts and self-aligning ferrules.
Sample Line Connections:
Connectors accept ¼” OD rigid or semi-rigid tubing.
UL, CSA pending
• Sample line probes.
• Orifice plugs (pulsation dampers).